When Lafayette LA home and business owners need air conditioner or furnace repairs or replacement, they call Smith Air Conditioning. That’s because we make customer service our top priority. Read our reviews below to find out more about the quality HVAC work we’ve done for your Lafayette LA neighbors.
HVAC Contractor Reviews Lafayette LA
for Lafayette, LA
Our Reviews by City
Good service. Detailed information. Good advice. Friendly service
Carrol - Lafayette, LA
Excellent service, affordable repair
Ann - Lafayette, LA
Great service, prompt response on weekend
Minnette - Lafayette, LA
Very good service know what they are doing
Raymond - Lafayette, LA
I will recommend Smith sir to my friends
Great Service, Fast Response
Beverly - Lafayette, LA
Shelly - Lafayette, LA
Cody was very nice and professional
Courteous, competent serviceman
Harriet - Lafayette, LA
Dawn - Lafayette, LA
Greg - Lafayette, LA
Randy - Lafayette, LA
AJ - Lafayette, LA
Great. Very timely and courteous. Fixed the problem in no time.
Beverly - Lafayette, LA
Professional and personable. Great job!
Erin - Lafayette, LA
Great service done in a timely manner.
Regina - Lafayette, LA
Great service!! We could not be happier.
Sarah - Lafayette, LA
We love, love, love our new air conditioner. My husband likes things done "the right way", and he is very impressed with the attention to detail and high standards that Smith Air Conditioning offers. I just love the cold air. Plus, the installation crew did a fantastic job installing the unit and ducts while keeping our house as clean as possible.
Robbie - Lafayette, LA
Too long from time agreed to move generator till final hookup.
Response from Smith Air Conditioning :
Robbie, I completely agree, it took much too long to get that job completed. That is one reason that I like to keep as much of the work "in house" instead of having to depend on other subcontractors. Thank You very much for your patience and your honest feedback. Scott
Val - Lafayette, LA
Fast service, professional
Did service call on trand unit and installed return grill 18_25_1
Performed full system check on 4 units
Run capacitor discharged. Replaced. Unit low on freon. Added.
Capacitor discharged. Replaced and checked unit.
Replaced condensate pump and checked operation of system.
Sealed grills and checked airflow
Did service call on Lennox unit and replace evap coil in warranty.
Found broken wire inside condenser repaired and checked system.
Installed in warrenty evaporator coil
Did service call on Lennox unit and added Freon and replace thermostat.
Performed maintenance agreement. Unit low on freon. Added. Run cap discharged replaced.
Replaced closed txv. Checked unit.